The cooling medium is flowing in the pipe of the cooling tower coil, the heat of the medium transmit to the wall of the pipe.
The fan on the top of the cooling tower exhausting air, outside cycling spray water touched with the wind which is extracted by the fan, latent heat and sensible heat make a exchanging, the temperature of the spray water cooled down, the cooled spray water formed a water film on the pipe wall outside to absorb the heat of the pipe, to take the medium heat way, reached the aim of cooling.
The internal fillings of the cooling tower can help cooling the circling water. In the progress of the heat changing, the internal medium not touched with the air directly, so that can keep the original character, no pollution, no attenuation, and volatilization. The spray water collected in the bottom pool, recycled.
1, Adopt the heat dissipation filling together with the heat exchange pipe to remove heat, good effect, small space.
2, The shutter at the air inlet, avoid the sunshine inject to the inside of the tower, avoid the algae breeding, keep the spray water clean.
3,The heating exchange pipe is T2 purple copper pipe, designed standby pressure 1.6Mpa, keep the medium not be pollution.
4,In the wall there is the checking door which is easy for maintain the spraying nozzle, fillings, ball float valve etc.
5,The fan is aluminum axial fan, the speed of the air flow is high, avoid the hot air return, low noise.